Adjust Tower Fundation For 3kw Tower Construction / Installation
In accordance with the construction drawings and site conditions,
determine the scope and objectives need to be monitored firstly,
then determine a reasonable installation location, obtain the exact
coordinates of the point and make a record.
Remove ground surface debris, according to the point that draw a
line through the determined definitively pit length and width, then
mechanical or human excavation. To pit depth is generally
permissible deviation of + 100mm, -50mm.
3,Tower Lifting and installation
3.1,In order to make sure that the main stem of verticality, before
lifting, please adjust all nuts of the bottom mounting plate to
meet the same horizontal plane.
3.2 Before the lifting, considering the center of gravity about
whole tower, the stress point of lifting operation must be higher
than the center of gravity
3.3 Hoisting parts choose the position as high as possible, so that
can reach a larger vertical degree when installation.
When axis body placed on the ground tighten the nuts firstly,
install all based screws as soon as possible, and adjust nuts at
level meanwhile. Secondly, Both the peak and the bottom of the axis
should perpendicular to the ground.
Generally, two 90 - degree direction of messenger wire as main
measurement method. If eccentric, pole body should be tighten bolts
from far side of the center of gravity.
Note: the higher lever, the greater the sensitivity adjustment.
After the anchor bolts, should prevent illegal loose nut. The
common practice is to use double nuts to prevent loosening.
4,Hoisting of Wind turbine
4.1,The crane will hoist wind turbine to meet the strut top flange
centre, three cables from wind turbines through and lead to the
tower connection at the bottom of the hole
4.2 Adjust the position of wind turbine, make its flange with the
strut top flange and insert the bolt hole location.
4.3,After confirm all cables are properly connected, locking bolts.
(5),Control cabinet installation
5.1,Control cabinet near the foundation part of the wind turbine
installation, fixed control cabinet on the base
5.2,The position of control cabinet should be based on a concrete
foundation, and embedded anchor bolts at a fixed cabinet .
5.3,Line pipes and interfaces are not exposed ,cables between
control cabinet and the tower through embedded galvanizing line
5.4,Wiring connection system according to the wiring diagram.
(6),Debugging and Commissioning
1,Idling inspection before debugging, including:
1.1,Grounding resistance test
1.2,The line insulation resistance testing
1.3,The performance test of distribution cabinet, wind turbine
1.4,The detection of hydraulic braking system
1.5,System debugging both on controller and pneumatic reduction
1.6,On-grid inverter debugging
2,Once the idling test of wind turbine finished, It enters into the
on-grid system debugging and commissioning stage.
2.1,Standby without wind, the cutting-out period in strong wind ,
normal reset time should not included during whole testing .
2.2,During the period of 48 hours commissioning, down time for more
than 1 hour or cumulative failure time more than 2 hours, 48 hours
to commissioning, timing again.
2.3,Wind turbines in commissioning qualified can put into